PRODUCT DESCRIPTION :-
Electrical Insulation Mat are generally used for covering the floor below the control panels. Our High Voltage Mats are manufactured as per latest Indian Standard i.e IS 15652:2006. The insulating mat that we offer is mainly used for safety of workers while installing and operating electrical equipment because of possibility of leakage of current.
These Insulating Mats are manufactured using elastomer (latex,rubber and elastomeric compounds that might be natural, synthetic or mixture of both) all along with anti-skid aberrations on the top to avoid slippage and smooth, lower surface . It is available in 2mm, 2.5mm & 3.0mm thickness depending upon the working/use voltage. Manufacturer’s Test Certificate is provided along with the supply.
TECHNICAL FEATURES :-
1. Fire Retardant.
2. High Di-Electric strength.
3. Good mechnical properties to withstand load and movement of breaker trolleys and associated electrical equipments.
4. Manufactured without any metallic derivatives.
5. Suitable for both A.C, & D.C, electrical installations.
6. Easy to install and pasted.
7. Water and moisture proof, does not decay.
8. High tensile strength and elongation properties.
WHY and WHERE These Electrical Mats are Recommended?
These electrical mats are highly recommended for total safety of workmen from electrical shock when working in or around environment like High Voltage Panels, Sub-station, Power Transformer Rooms, LT & HT labs , near Busbars, near Control Panels etc. Safety from electrical shock is required for workmen whether they are involved in Electricity Generation, Transmission, Distribution or its use.
TECHNICAL DATA SHEET :-
|SIZE||1 Meter Wide X Any Length (Standard 10 Meter).|
|COLOUR||BLACK/BLUE/RED (other color like , Red, Grey, Green, Yellow Etc. as agreed mutually with suppliers/End User|
|TENSILE STRENGTH||For Temp. -10 to 55 C -15N/mm2(Min.)|
|ELONGATION AT BREAK||For Temp. – 10 to 55 C -250%(Min.)|
|INSULATION AT BREAK||10,00,000 (Min.)|
|FLAME RETARDANCE||The Mat is retarded to fire|
|LOW TEMPERATURE||No tear, break or cracks is observed in Mats under force of 100N for 30 seconds at -10 plus minus 3 C|
|AGING TEST||@70 C plus minus 1 C For 168 Hrs|
|1. TENSILE STRENGTH||Not less than 75% of the corresponding value of unaged sample|
|2. ELONGATION AT BREAK||Not less than 75% of the corresponding value of unaged sample|
|EFFECTS OF NaOH/H2SO4||@Room Temperature for 48 hrs|
|CLASS OF MATS||THICKNESS||DI-ELECTRIC
|A||2.00 mm||30 KV||3.3 KV|
|3.||C||3.00 mm||65 KV||